Home › Electrical Engineering Forum › General Discussion › Thermal Magnetic Circuit Breakers › Re: Thermal Magnetic Circuit Breakers
2014/12/10 at 12:30 am #13619
A house crt. rated at 15 A. Should it trip say when the ammeter reaches 15.2 or 15.5 or 16A. If so what adjustments are available to make it trip at any particular setting? The crt. is brand new and will not trip even at 40 amps. what causes can possibly cause this mulfunction?