Home › Electrical Engineering Forum › General Discussion › KW Calculation › Re: KW Calculation
2010/11/30 at 8:11 am #11649
If I get your question right, you are asking for the available power at the end of 35km distance? the “load end power” will depend on the size of your conductor in this 35Km distance and this can be calculated using the voltage drop equation. In addition, the type of load (motors, resistive load, etc) should also be considered.
Moreover, available power will never increase at the end of the line.