- 2016/04/14 at 11:20 am #11304Steven MillParticipant
Hi everybody, it’s Steven Mill. I know it’s been a while since I haven’t published an article on the blog, but here I am. Today I want to tell you about underground cable faults and how to detect them. Ready?
In a power transmission and distribution system, cables serve the primary purpose of transmitting electrical energy from one point to another. A fault at any section of the cable system significantly reduces the functionality and integrity of the whole setup. This situation significantly escalates with underground cables, due to the location. With the power systems growing rapidly over the years, the number and length of cables has increased over the years…
Other than the obviously higher cost than overhead cables, the location gravely affects cable fault detection, location and attendance. Well, unearthing the whole cable for checks, while it may work, is expensive and unnecessary. The challenge therefore is to find fault detection methods that are less ‘evasive’.
Detecting underground cable faults: the whole process
The following are the common ways to detect underground cable faults:
This is perhaps one of the most rudimentary and destructive ways to detect cable faults.it involves digging up the cable, and cutting it into sections, followed by inspecting and testing each section for faults.
It involves introducing a high voltage (25kV) on one end of the cable to induce a high current arc in the faulty cable. The arc occurs at the fault location, and at such a high voltage, it is high enough to cause a thump sound that is audible above the ground. Well, suffice to say there are drawbacks:
- One, it is hard to access such high voltage for low-medium priority testing, though there are commercially available surge generators.
- Secondly, the mere fact that there are better methods out there. Thirdly, the method is cumbersome, and ineffective to use for long cable lengths.
Transmitter and receiver method
It consists of an AC generator that supplies the signal current to the underground pipe, and a receiver that detects the electro-magnetic field from the signal current. In many instances, the transmitter also contains information on the amount of resistance that the current circuit carries.
Time domain reflectometry
Also referred to as pulse echo method, enables the tester to measure the distance to any changes in the cable. A pulse of radio frequency is introduced on one end of the cable, and then an integrated timer measures the frequency travel along the cable. The timer stops when the frequency is reflected back.
There are standard values for various materials used in cable construction for various lengths. With this information, the tester can be able to pinpoint the point of disparity accurately based on the time. Do note that a fault changes a cable impedance, and thus, the ability to transit pulses.
The information required for accurate pinpointing include velocity of propagation, maximum distance that can be displayed on the TDR display and pulse width.
Regardless of the method used to detect an underground cable fault, accurate pinpointing of the fault is as crucial. Engineers and testers use microphones and sound amplifiers for an accurate location.
Usually, the acoustic equipment has range interface, or counter, so that the user can pinpoint the area with the highest sound. The assumption is that the sound travels up unimpeded by either roots or rocks.
Thanks for reading,
Very nice article! Do you have other advices to give? Share them in the comment section.2016/04/17 at 5:10 am #13777wajahatParticipant
Steven thankyou very much for this quintessential article your work is really admireable.
But sir i have little bit confusion if there is short circuited fault(line to ground)
then how TDR will be helpful to trace the fault location.2016/04/19 at 11:03 am #13778George TwumasiParticipant
Good one there.. I’m new here…
Thanks Sir2016/06/18 at 8:24 am #16469angela002Participant
I AM INTERESTED TO INVEST WITH YOU IN YOUR PROPERTY/ESTABLISHMENT IN YOUR COUNTRY WITH TOTAL TRUST BUT HOPE THAT YOU WILL GIVE ME TOTAL SUPPORT,SINCERITY AND COMMITMENT.PLEASE GET BACK TO ME AS SOON AS POSSIBLE SO THAT I CAN GIVE YOU MY PROPOSED DETAILS OF FUNDING AND OTHERS.
ANGELA MARCO2017/09/22 at 6:13 am #18440pradeepkumarParticipant
This type of fault is better than short circuit fault, because when the open circuit fault occurs, then the flow of current through an underground cable becomes zero. Once check whether the circuit working or not.
- You must be logged in to reply to this topic.